- ductile cast iron
- cast steel
- stainless steel
- Super Duplex
- DN15 to DN65 (1/2“ bis 2 1/2“)
- PN16 to PN40
- outlet pressure: 0,5–20 bar
- with stainless steel bellow 1.4571
- for liquids, gases and steam
- EN-JS1030, 1.0619, 1.7357, 1.4408, 1.4469
Pressure regulating valve – T679
self-operated, for steam, fluids and gases
The function of pressure regulating valves (pressure reducing valves) is, to reduce a varying or constant upstream pressure (inlet pressure) of the media to a constant reduced pressure (outlet pressure, back pressure) which is independent of the upstream pressure.
The pressure reduction occurs by throttling the free cross section between the seat and cone. Via a pulse line, which is already installed on the valve, the reduced pressure presses on a control piston. As a result, any change in pressure on the downstream pressure side is immediately converted into a lifting movement of the valve cone.
The valve is well suited for intermittent consumption. At zero consumption, that is, when the consumption on the downstream pressure side is zero, the valve closes safely by low pressure increase.
The pressure reducing valve T679 is suitable for compressible media, e.g. steam, compressed air, natural gas, nitrogen, as well as for incompressible media, e.g. water, oil, fuels, LPG (propane, butane) etc.
They are mainly used in industrial plants, plant engineering and process engineering.
Pressure reducing valves can be supplied with flanges, weld ends or threaded connections.datasheet Operation instruction back
Installation length acc. EN 558-1
Flanges acc. to (DIN, JIS, ASME, ANSI)view dimensions
SCHLEY ARMATUREN GMBH - COMBINES TRADITION SINCE 1913 AND MODERNITY
Your application - our solution.